Now showing items 1-3 of 3
On the assessment of harmonic emission in distribution networks: opportunity for the prevailing harmonic phase angle
Harmonic emission assessment for Grid Code compliance of Renewable Power Plants (RPP) has to be fair and pragmatic. The CIGRE C4.109 method lacks the ability to determine which harmonic currents have a positive or negative ...
Evaluation of harmonic distortion from multiple renewable sources at a distribution substation
Harmonic emission assessment in a distribution network with existing background voltage harmonics is a challenge for Renewable Power Producers (RPP) aiming to achieve grid code compliance. Dynamic interaction of harmonic ...
Impact of aggregation interval on harmonic phase angle measurements
The aggregation principles of IEC 61000-4-30 is a well-known concept implemented in Power Quality (PQ) recorders. Only rms data is retained. Harmonic emission assessment requires the analysis of harmonic phasors. Continuous ...